1. Introduction and Informational video
Click a link below to see and hear the inventor describe the UV-C unit in this no-nonsense, no-hype informational
Choose your connection speed:
High-speed Internet connection (Cable modem or DSL)
Download the above video to your computer, for playback
Windows Media Player: Introduction video (56K dial-up)
2. Installation video
After viewing the intro video above, click on a link below to see and hear how to install the E-200 UV-C
Air Probe Sanitizer in different typical
Choose your connection speed:
High-speed Internet connection
(Cable modem, DSL)
Dial-up 56K modem
Download the above video to your computer for playback
Windows Media Player: Installation video
* NOTE: the installation of these products, as easy as it may look on the video, should be
performed only by a qualified licensed heating and air conditioning professional.
(Installation usual only takes a few minutes. See for yourself: watch the
No high-bandwidth Windows Media Player videos are available.
Sorry, our video guy did create them for us, but they are not only enormously huge files (90 to 155
megabytes), but they are not near the quality of the RealPlayer files above.
Clarifications to the Air Probe Sanitizer video
At the time the video was made, some of the ways that UV-C helped destroy dust, odors, and
volatile organic compounds (VOC's) were not clearly understood. Negative hydroxyl
ions are not mentioned, only
negative air ions. You can read about hydroxyl here.
The "Flush Mount" unit: no reference is made in the video to a model number. The model FME-200 is
in the video. Also, the sockets are now mounted 90 degrees to the position shown on the FME-200 in the video. The current design FME-200 is correctly shown
on the web site photos.
References to 120 volts and step-down transformers are now all but obsolete. The latest design Air Probe Sanitizers
now have an electronic ballast which automatically adjusts the current for any input voltage between 103 volts and 280 volts.
The slot size mentioned for the model T-200 is 4" x 17". We suggest that the slot length be about 15"
and not 17", as the standard model is 17" long.
It is recommended that any existing wires (that may not have UV-resistant insulation)
be covered with something to prevent deterioration over time by the UV rays, such as duct tape or black split loom tubing.
You should also read and follow the instructions that we include with each Air Probe Sanitizer.
These videos load quickly and have good picture and sound quality regardless of your
Internet connection type.
RealPlayer videos are usually superior and preferred over Windows Media Player. To view the
RealPlayer streaming videos, you must have RealPlayer® version 8 (or later) installed on your computer.
Most people already have it installed. If you don't...
RealPlayer® 8 (Free download)
A VHS training video is also available. The videos on this page were taken directly from this
videotape, so you do not need this tape unless you cannot view any of the video presentations on this page for some reason.
IMPORTANT INSTALLATION NOTES
These very important points may not be apparent from
watching the video:
1. The units must be installed on the COLD AIR SIDE of the cooling coil
(the evaporator or A-coil). The reasons: if they were installed on the inlet side of the
cooling coil instead of the side where the cooled air exits, negative ions would be trapped by the
coil fins instead of exiting out of the duct vents in the rooms. Also, mold and mildew growth would
not be effectively controlled.
2. The units must be ALSO be installed close to the coil so that
the UV light shines on as much of the coil and condensate drain pan as possible. The reason: the cooling coil
and condensate (water) catch pan is where mold,
slime, and bacteria normally grows, and the UV light has to shine on the coil in order to prevent this and
keep the coil clean.
The installations shown in the installation video are upflow systems, and the
units are downstream (on the cooled air side) of the coils. if you are
installing them in a downflow system, you cannot place them as shown in the video. In that case,
they might be installed in the plenum below the cooling coil rather than as shown.
The power to the Air Probe Sanitizer should remain on to avoid shortening the life of the lamps.
The enclosed normally-open cover switch should be installed so that power to the Air Probe
Sanitizer is removed when the access panel is opened.